High Performance Photoluminescent Safety Products
Photoluminescent Exit signs are in the category of an Internally Illuminated Sign. The signs are permitted, provided they are listed in accordance with UL 924, "Standard for Safety Emergency Lighting and Power Equipment" and meet all the requirements outlined in the criteria from the Life Safety Code 101, 2006 edition parts 22.214.171.124. Our product line meets the requirements set forth by the ICC in the International Building Code (IBC). To purchase our product please Contact Us direct for a list of official distributors
Requirements for Exit Sign Illumination
NFPA 101 defines the methods of illumination for exit signs:
Externally illuminated - the light source is contained outside of the device or legend that is to be illuminated. The light source is typically a dedicated incandescent or fluorescent source;
Internally illuminated - the light source is contained inside the device or legend that is illuminated. The light source is typically incandescent, fluorescent, electro luminescent, light-emitting diodes, or photoluminescent;
Photoluminescent - the sign is illuminated by self-contained power sources and operates independently of external power sources. (Batteries do not qualify as a self-contained power source.)
Photoluminescent - The face of the sign must be continually illuminated while the building is occupied. The face of the sign shall be illuminated according to its listing from the face of the sign. The illumination has to be a reliable source as determined by the Authority Having Jurisdiction, AHJ. The AHJ is the ultimate arbiter concerning safety practices and safety equipment for a particular locality. The charging light must be of the same type that is specified on the sign.
Photoluminescent Signs need a specific type of light and a minimum level of light on the face to assure that the sign will be able to provide adequate illumination in an emergency situation. During illumination the sign shall not be connected to an automatic timer.